|Place of Origin:||China|
Payment & Shipping Terms:
|Minimum Order Quantity:||1set|
|Packaging Details:||Wooden case|
|Delivery Time:||35 days after got deposit|
|Payment Terms:||T/T, L/C, D/A, D/P, Western Union, MoneyGram|
|AHU Type:||Celling Type||Power Supply:||380V 3ph 50hz|
|Air Flow Range:||2000~50000m3/h||Double Skin Panel:||25/50mm PU Insulation|
|Fan Type:||AC Direct Drive Fan||Function:||Air Conditioner Terminal Unit|
|Air Coil:||Al Fin||Static Pressure:||150-500Mpa|
|Air Valve:||Manual Or Automatic|
Humidistat Modular Air Handling Units,
Thermostatic Modular Air Handling Units
Modular thermostatic and humidistat air handling unit for pharmaceutical plant
1. Air return: Cooling: Air in 27℃ DB; Air in 19.5℃ WB. Heating: Air in 21℃ DB.
2. Fresh Air: Cooling: Air in 34℃ DB; Air in 28℃ WB. Heating: Air in 7℃ DB.
3.Chilled water in/out:7℃ /12℃.
4. Hot water in/out: 60℃/50℃.
1) The unit is designed as structure compact, good looking, low noise, light weight;
2) Adopt nylon-web plate filter, providing convenient drawing;
3) The centrifugal fan with double inlets is used to keep it running stable and with less noise;
4) The condensed water tray is made of stainless steel or galvanization steel, free from rust and erosion;
5) It can be matched with protection device and invert.
1/Both supply fan and exhaust fan are built inside tobring in fresh air and exhaust out the stale
indoor air as well, thus to keep indoor space in natural comfort. 2/Built-in heat exchanger
(rotary heat exchanger or plate heat exchanger) transfers energy contained in the outgoing
indoor air to the coming fresh air,thus fresh air is precooled or preheated. 3/Various
functional sections such as filter section,cooling/heating section, humidifying section etc.
Our equipment is warranty for 1 year excluding consumable parts and accessories.
All equipment is shipped with a comprehensive use’s manual complete with a report documenting all test procedures.
Additional IO/OQ/GMP document is available upon request.
Contact our sales representative for specific warranty details or document request.
Consumable parts illustration:
1: Pre-filter: each one should be replacement in each 6 month, but it can refresh no more three times.
2: HEPA air filter: each one should be replacement in each half and one years.
Standard export packing:
--Stretch film strapped whole cabinet,
--Foam inside protected,
--Plywood case solid fixed
Enter Your Message